GE Power Controls SOLID STATE SOFT STARTER ASTAT Plus USER MANUAL REMARKS: 1. Read this manual throughly before using the ASTAT Plus, and. General Electric/Motor Starter MPN ASTAT-QI3KDP ASTAT Plus Solid State Soft Start 50 HP Model: ASTATQI3KDP B &. Max Volts 3 Phase AC: VAC. Find great deals for GE ASTAT Plus Qi3kdp 50hp Soft Start General Electric 50 HP Starter. Shop with confidence on eBay!.
|Published (Last):||7 August 2007|
|PDF File Size:||10.19 Mb|
|ePub File Size:||20.30 Mb|
|Price:||Free* [*Free Regsitration Required]|
You should use an external overload protection if required by local rules or to protect the motor against current imbalance. A tacho generator must be used as feedback. Please provide Ye the necessary paperwork already filled out 1 business day ahead of pickup. Note however that the parameter “txxx” will show astaat latest entry, which may differ of actual voltage value. The best-known are star-delta starters, autotransformer starters, stator resistance starters or using part winding motors.
GE ASTAT Plus Qi3kdp 50hp Soft Start General Electric 50 HP Starter
Special financing available Select PayPal Credit at checkout to have the option to pay over time. From this it can be deduced that any start with reduced voltage reduces the torque in squared proportion to the voltage per motor phase.
This speed feedback signal is required when the “linear ramp” function is used. Other offers may also be available.
Command signal may be provided by one NO free voltage push-button to terminals 1 and R ; if for instance the response is R, this means that the overload curve selected is IEC class Once this function is enabled, the relay 2r is automatically assigned to this function check section This is usefull to stop a fan which is plys in reverse at the starting time For additional information, see the Global Shipping Program terms and conditions – opens in a new window or tab No additional import charges on delivery Delivery: Shipping Outside the US Buyer is responsible for all duties, customs and taxes.
Once this function is enabled, the relay 3r is automatically assigned to this function. On larger orders and in extreme circumstances we may need more time. An item that has been used previously. Environment When installing equipment, keep the following points in mind: Learn more – opens in new window or tab pluw Money Back Guarantee Get the item you ordered or get your money back.
In this case the bypass is automatically done after starting. For additional information, see the Global Shipping Program terms and conditions – opens in a new window or tab This amount includes applicable customs duties, taxes, brokerage and other fees.
Refer to local applicable electrical codes. Shipping via USPS international is at your own risk: Slow speed and normal run commands are internally interlocked. The programmable inputs I3, I4 are not assigned to any function as default. Internal error Microcontroller malfunction Check IC1 and IC8 are correctly inserted in their sockets Long start time Current limit condition present more than 2 x ta sec. Visit my eBay store. It should be provided by a DC tacho-generator coupled to the motor.
Adjustments are very easy to make and diverse options may be selected to have equipment capabilities suited to application needs every time. X – Unit frame rating F,G,H, Start-up – Make sure equipment wiring corresponds to one of the recommended routing diagrams or equivalent – If the motor does not have thermal protection sensor, a link must be set beetwen terminals 5 and 6 – Make sure the control wire harness corresponds to the control voltage used.
The slow speed function may be enabled by setting “Jxxx” to I3. Ralentissement courant continu peut provoquer la surchauffe de moteur.
GE ASTAT Plus QI3KDP 50HP Soft Start General Electric 50 HP Starter | eBay
Remarks Supply wire conductors should have the same section as direct starters. This area includes the starting of pumps, fans, conveyor belts, etc. Learn more – opens in new window or tab. Learn More – opens in a new window or tab Returns: Delay trip time The unit trips if the line voltage increases above of the percentage set.
If you need items quickly let us know directly to make sure we get them out for you!